Views:2 Author:Site Editor Publish Time: 2018-05-02 Origin:Site
Diesel Generator Operation Manual Control System Part 9
If the Adjust button in Menu Bis pressed, theAdjust submenu will appear (Figure 9-1).
The Adjust submenu is intended for qualified service personnel and site personnel only and may require a USER password. If a password is required, the USER password menu will appear when you try to modify the Adjust submenu. (Refer to Password Menu in Section 4.11 to enter password).
Changes are automatically saved when you exit this menu.
Note: Use the + and - buttons to increase or decrease the values in the following fields. Use the arrow (®) button to move the cursor within a field or to the next field. Selected field is highlighted.
•START DELAY: This delay applies only to remote starting in the Auto mode.
The Start Delay adjustment range is 0 to 300 seconds.
•STOP DELAY: This delay applies only to remote stopping in the Auto mode. The Stop Delay adjustment range is 0 to 600 seconds.
•VOLTAGE: Used to adjust the output voltage ±5%.
•FREQUENCY: Used to adjust the frequency ±3 Hz.
•VOLTAGE/SPEED DROOP:These two sub-menus apply to a generator set that has the paralleling option enabled and is configured to operate in droop mode. These adjustments must be performed by technically qualified personnel only.
Figure 9-1Adjust Sub-menu