Views:2 Author:Site Editor Publish Time: 2018-04-28 Origin:Site
Diesel Generator Operation Manual Control System Part 3
Menu Units Selection
During any control panel operation, you can change how units are displayed by pressing the two lower menu buttons (one on each side of display). When pressing these two buttons simultaneously, the unit’s submenus will appear (Figure 3). After selecting the desired units, press the ENTER button in this submenu to change and save the selections.
Note:Use the + button to select the desired option for each field. Use the arrow (®) button to move to the next field. Selected field is highlighted.
Figure 3Units Submenu
This selection must be set to Local, when the graphical display is mounted on the generator set front control panel, or Remote when mounted remotely from the generator set.
The Local/Remote selection determines which buttons in the Control submenu (Section 4.7) are active (displayed).
Temp: Used to select °F or °C for temperature readings.
Pressure Fluid: Used to select PSI, KPa, BAR or IN for pressure readings.
Pressure Gas: Used to select INHG or MMHG for pressure readings.
Flow Air: Used to select CFM or CMM for airflow readings.